The photocontrol JL-106, JL-116 and JL-126 are applicable to control the street lighting, passage lighting and doorway lighting automatically in accordance with the ambient lighting level.
They are designed on the basis of electrical heating structure that provides time delay over 30 seconds to avoid redundant switching against spotlight or lightning during the night time. A temperature compensator system provides consistent performance regardless of the ambient temperature.
They are convenient for direction adjustment after installation once an additional swivel is applied.
Disconnect power, place screw thread of the SWITCH in knockout hole and fasten with rubber gasket and Zinc alloy lock-nut.
Wire according to the diagram in right hand.
Slide the mounted adjusting metal strip to have preferred On/Off levels, if necessary.
Do not install the switch with the Photocell facing artificial or reflected light. This will cause the unit to cycle on and off at night.
It is normal for the SWITCH to take several minutes to turn off when first installed.
To test “turn on” during daytime, cover its eye with sliding the metal strip mounted.
Do not cover with finger because light traveling through fingers may be great enough to keep the switch open.
Test will take approximately 2 minutes.