All the JL-230 series receptacles are intended to be pre-mounted onto those lanterns designed to fit an ANSI C136.10-1996 twist-lock photocontrol.
Both JL-230-16 and JL-230-14 have been recognized by UL to applicable US and Canadian safety standards, under their file E188110, Vol.2.
|Applicable Volt Range||0~480VAC|
|Power Loading||AWG#14: 15Amp max. / AWG#16: 10Amp max.|
|Optional Signal Loading||AWG#18: 30VDC, 0.25Amp max.|
|Ambient Temperature||-40℃ ~ +70℃|
|Overall Dimensions (mm)||65Dia.x 40||65Dia.x 67|
|Accessory||Rear Cover||● R option||●||● R option|
|Wall Mount Bracket||-||-||
6” Min. (See Ordering Information)
Disconnect power; wire the receptacle according to the diagram below. An arrow indicating NORTH on the top of the receptacle is used to assist correct direction. Push the photocontrol on and turn it clockwise to lock into the receptacle.
Adjust the receptacle position if necessary.
JL-240Y series supports tool-free rotation.
JL-240Z series supports Wall-mount and rotation.
It is normal for the SWITCH to take several minutes to turn off when first installed.
To test “turn on” during daytime, cover its eye with sliding the metal strip mounted.
Do not cover with finger because light traveling through fingers may be great enough to keep the switch open.
Test will take approximately 2 minutes.